ASHRAE publishes 2013 version of IAQ standard
The 2013 version of ASHRAE’s indoor air quality (IAQ) standard contains several revisions to help users better meet its requirements.
Newly published, ANSI/ASHRAE Standard 62.1-2013: Ventilation for Acceptable Indoor Air Quality, sets minimum ventilation rates and other requirements for commercial and institutional buildings.
The 2013 standard combines the 2010 standard and 10 published addenda to that edition, providing an easy-to-use consolidated standard. Specific information on the contents of each addendum and approval dates for each addendum are included in Informative Appendix J at the end of the standard.
The 2013 edition of the standard revises and improves the standard in several ways. A number of changes remove inconsistencies within the standard and improve clarity. Significant changes include:
- Table 6-2, Zone Air Distribution Effectiveness is modified to increase the ventilation effectiveness of underfloor air distribution systems that meet certain conditions.
- Requirements for the quality of water used in humidification systems are modified and clarified.
- Building level pressurization requirements were clarified, including adding a definition of “exfiltration.”
- A performance alternative to the prescriptive exhaust rates is added. This approach differs from the Indoor Air Quality Procedure, the existing performance-based method for setting supply ventilation rates, in that monitoring of the concentrations of contaminants of concern is required and provides the basis for control of exhaust flow rates.
- Some changes to the ventilation rates and space types in Table 6-1 are made. These add refrigerated warehouses and change the ventilation rate for sports related spaces to include a per occupant component which then allows the use of demand controlled ventilation in these spaces.
- The filtration requirement on air entering wetted cooling coils has been modified to change the MERV rating from 6 to 8. This change will reduce potential for particulate deposition on the coils that could lead to biological or other contamination on the coils.
- Toilet exhaust air that is cleaned to Class 1 may be recirculated.
Case Study Database
Get more exposure for your case study by uploading it to the Control Engineering case study database, where end-users can identify relevant solutions and explore what the experts are doing to effectively implement a variety of technology and productivity related projects.
These case studies provide examples of how knowledgeable solution providers have used technology, processes and people to create effective and successful implementations in real-world situations. Case studies can be completed by filling out a simple online form where you can outline the project title, abstract, and full story in 1500 words or less; upload photos, videos and a logo.
Click here to visit the Case Study Database and upload your case study.