Controllers: Advantech launches a new generation of PACs
Dual controllers separate HMI and software-based logic tasks, and a backup system enhances reliability for APAX-5000 series PACs.
The Industrial Automation Group of Advantech has introduced a new generation of programmable automation controller (PAC), the APAX-5000 series, which integrates control, information processing, and networking in a single system with a unique dual controller architecture.
Advantech's APAX-5000 series consists of controllers, I/O modules, backplanes, and power modules and features a unique architecture: two standalone CPU modules working together, responsible for different tasks. One provides high computing power for HMI/SCADA, recipe, database and communication tasks (APAX-5570XPE or APAX-5571XPE), while the other is dedicated to software-based logic for I/O tasks (APAX-5520KW). This means that if the HMI/SCADA controller crashes, the I/O processing won't be affected. Engineers can simply check the HMI/SCADA controller and maintain it, without having to worry about the I/O processing tasks. This can prevent unexpected stoppage, decreases operational risks, and ensures higher reliability for critical control tasks.
APAX-5000 controllers also support backup functions by storing the same I/O processing program on two controllers. One will execute the I/O processing and if that controller fails, the second controller will automatically take responsibility for I/O processing within 1.5 seconds. Users don't need to write programs for this mechanism and the backup system enables reliability for critical applications, according to Advantech.
The APAX-5000 I/O modules are designed to be hot swapped when the system is powered-on and running. I/O modules are equipped to be either local I/O or remote I/O through their Ethernet bus backplane. APAX-5000 PAC offers one and two slot backplanes, each with one expansion port. Using a standard Ethernet cable to connect the expansion port on the two backplanes, a remote expansion with local-bus speed is built with a distance up to 100 m. In addition, any standard Ethernet switch can be used between the two backplanes.
The implementation of Ethernet switches not only enhances the flexibility of I/O expansion, it also increases the expansion distance. For example, if there are three Ethernet switches between two I/O stations, the expansion distance can be at least 400 m. (When fiber optic ports are available on the Ethernet switch, the distance can be much longer.) Therefore, users can build line, tree or star topologies for I/O expansion - all with fast local-bus speed.
The APAX series offers complete scalability functions that the system can easily upgrade by changing controller with difference processor (higher performance). This means users don't need to re-write any program if they want to upgrade the system.
- Edited by Renee Robbins, senior editor
Control Engineering News Desk
|Search the online Automation Integrator Guide|
Case Study Database
Get more exposure for your case study by uploading it to the Control Engineering case study database, where end-users can identify relevant solutions and explore what the experts are doing to effectively implement a variety of technology and productivity related projects.
These case studies provide examples of how knowledgeable solution providers have used technology, processes and people to create effective and successful implementations in real-world situations. Case studies can be completed by filling out a simple online form where you can outline the project title, abstract, and full story in 1500 words or less; upload photos, videos and a logo.
Click here to visit the Case Study Database and upload your case study.