Energy savings: Right-sizing electric motors could save billions in energy annually
Energy efficiency losses through over-sizing of pump electric motors by engineers are commonplace, according to WEG Electric Motors.
Atlanta, GA — “Industry figures suggest that around 80% of pump motors could be the incorrect size,” commented Andrew Glover, product manager for WEG Electric Motors , a global supplier of motors, drives, controls, generators, and transformers. “The majority are over specified by as much as 10 or 15% by engineers wanting to be‘on the safe side.’ As pumps typically account for around 30% of an industrial country’s energy usage, this represents a serious loss of energy. Electric motor manufacturers are forever striving to increase energy efficiency by one or two percentage points, but incorrect specificationby an application engineer can mean that is wasted effort.”
Glover explains that his figures take no account for the extra cost of a larger motor with all the associated equipment, drives, cabling, etc. “A single percentage point increase in energy efficiency,” he says, “can save the equivalent of the purchase price of an electric motor over its design life, it seems ludicrous to waste energy through poor specification.”
Glover’s research indicates that under-sizing is also relatively common and should not be ignored. An electric motor can operate above its rated output, thus allowing for temporary overloads. However, such a motor will run hotter as a result, and overheating will cause damage and/or shorten its useful life. Two points where this can directly affect the motor life are the bearings, which influence the motor reliability, and the coil insulation. Overheating degrades the insulation more rapidly and encourages discharges, which further degrade the insulation, thus shortening the motor’s life.
Specification of motor size should, therefore, include starting condition as well as running torque. Method of starting is also important; direct on line starting methods will create high torque that also impose mechanical stresses on the pump and hydraulic components, while star delta starting delivers lower torque and current.
Glover suggests including a variable speed drive or soft starter in the system specification, matched to the requirements of motor and pump will easily overcome these problems. Variable speed drives also improve energy efficiency in the long term by matching application requirements with the correct motor speed and thus avoid energy wasted by, for example, belt drives, clutches and gears.
— Edited by C.G. Masi , senior editor
Control Engineering Machine Control eNewsletter
Register here and scroll down to select your choice of eNewsletters free.
|Search the online Automation Integrator Guide|
Case Study Database
Get more exposure for your case study by uploading it to the Control Engineering case study database, where end-users can identify relevant solutions and explore what the experts are doing to effectively implement a variety of technology and productivity related projects.
These case studies provide examples of how knowledgeable solution providers have used technology, processes and people to create effective and successful implementations in real-world situations. Case studies can be completed by filling out a simple online form where you can outline the project title, abstract, and full story in 1500 words or less; upload photos, videos and a logo.
Click here to visit the Case Study Database and upload your case study.