Kline Fitness Center Expansion, Dickinson College
Addition to existing building; Kline Fitness Center Expansion, Dickinson College; Barton Associates Inc.
Engineering firm: Barton Associates Inc.
2013 MEP Giants rank: 97
Project: Kline Fitness Center Expansion, Dickinson College
Address: Carlisle, Pa., United States
Building type: School (college, university)
Project type: Addition to existing building
Engineering services: Electrical/Power, Fire & Life Safety, HVAC, Lighting
Project timeline: November 2011 to June 2014
Engineering services budget: $180,000
MEP budget: $2.5 million
The Dickinson College Kline Fitness Center expansion presented several challenges including coordinating with the extensive fenestration on both exterior walls and roof, maintaining the client's construction budget, and designing effective mechanical systems while maintaining the desired architectural aesthetic. More than half of the exterior walls associated with the fitness center are glass. While this provided great opportunities for views and daylighting, it presented significant challenges in creating an environment that was both comfortable and energy efficient. The architectural aesthetic of the building also presented challenges. The space itself is an open steel structure, with the structural steel being part of the finished look within the space. This created difficulty in air distribution strategies.
Barton Associates addressed these issues through early and extensive use of building information modeling (BIM) and energy modeling. The firm collaborated with Cannon Design to reach the best balance between cost and performance. BIM allowed Barton Associates to understand the composition and components of the building very early in the project design. This was critical in meeting the client's budget and significant energy use index goals.
Significant shading elements as well as high-performance fenestration products allowed the building to use 30% less energy than a comparable baseline facility. One way the team overcame the architectural aesthetic of the building was to use a double wall system to serve as a vertical air distribution pathway around the core of the building. This allowed for air distribution while providing the added benefit of sound isolation between the squash courts and other occupied spaces. Additionally, Barton Associates took advantage of operable windows and skylights to create an active natural ventilation system. When outdoor conditions are suitable, this system allows for increased ventilation and free cooling of the space, thereby improving indoor air quality and reducing energy use.
|Search the online Automation Integrator Guide|
Case Study Database
Get more exposure for your case study by uploading it to the Control Engineering case study database, where end-users can identify relevant solutions and explore what the experts are doing to effectively implement a variety of technology and productivity related projects.
These case studies provide examples of how knowledgeable solution providers have used technology, processes and people to create effective and successful implementations in real-world situations. Case studies can be completed by filling out a simple online form where you can outline the project title, abstract, and full story in 1500 words or less; upload photos, videos and a logo.
Click here to visit the Case Study Database and upload your case study.