New snap-action air relay pressure switches
Family eliminates problems typical of throttling band designs, say K-Tek. New pilot-operated, snap-action pneumatic switch has a patented, snap-action mechanism that eliminates problems normally associated with throttling bands. This new-design air relay can be fine-tuned for accurate increasing or decreasing action. It has a narrow deadband, as low as ...<br/>
K-Tek has announced a new pilot-operated, snap-action pneumatic switch from Beta N.V., its subsidiary in the Netherlands. The switch features a patented, snap-action mechanism that eliminates problems normally associated with throttling bands. This new-design air relay can be fine-tuned for accurate increasing or decreasing action. The switch features a narrow deadband, as low as 10 mbar, and supports pilot supply and signal pressures up to 7.0 bar.
K-Tek says the new units are designed for valve control, bleed-off shut-down, or alarm applications, even in Zone 0 hazardous locations. The switch is available in two configurations: Type SA for normally closed (N.C.) and Type SB for normally open (N.O.) operation.
"A high-quality, self-aligning diaphragm piston sensor is at the heart of the Beta air relay switch," says Winston Landymore, Beta product manager at K-Tek. "Limited piston travel translates pressure at the diaphragm directly to actuation of the microswitch. This means no intervening linkages or mechanisms, and full protection against high over-range pressures up to 400 bar."
The unit’s piston sensor is isolated from the process fluid by a diaphragm and static O-ring seal, retained by a process connection port. These process wetted parts are available in a wide range of materials, eliminating the need for costly chemical seals. Process connections are available in 316 stainless steel, Monel, and aluminum. Diaphragm and O-ring material choices include Buna-N, EPR, Kalrez, neoprene, Teflon, 316 stainless steel, tantalum, Viton A, and Monel. A venting port avoids overpressure in the enclosure.
Also read: Safety: Tale of Two Applications .
—Edited by Peter Welander, process industries editor, PWelander@cfemedia.com ,
Control Engineering Process Instrumentation & Sensors Monthly
Register here to select your choice of free eNewsletters .
|Search the online Automation Integrator Guide|
Case Study Database
Get more exposure for your case study by uploading it to the Control Engineering case study database, where end-users can identify relevant solutions and explore what the experts are doing to effectively implement a variety of technology and productivity related projects.
These case studies provide examples of how knowledgeable solution providers have used technology, processes and people to create effective and successful implementations in real-world situations. Case studies can be completed by filling out a simple online form where you can outline the project title, abstract, and full story in 1500 words or less; upload photos, videos and a logo.
Click here to visit the Case Study Database and upload your case study.