On call 24/7: Wireless system detects open circuits
Cooper Bussman InVision system detects when a circuit protection device has opened, alerts maintenance personnel which device has operated (phone, text, email), where it is located, part number of the replacement device, and the appropriate level of personal protective equipment to wear to replace or reset the device.
St. Louis, MO - Cooper Bussmann InVision system detects when a circuit protection device has opened, alerts maintenance personnel which device has operated (phone, text, email), where it is located, part number of the replacement device, and the appropriate level of personal protective equipment to wear to replace or reset the device. It uses a proprietary wireless mesh system said to be 99.999% reliable; the company does a site assessment to ensure ease of installation.
First target markets are those in which downtime is particularly expensive : automotive facilities, pulp and paper, food and beverage and steel and aluminum. Kevin Knopf, channel marketing specialist at Cooper Bussmann, says older facilities with a large installed base of fuses may not even quantify costs related to fuses; a goal is to reduce the amount of downtime of the end user.
The InVision system includes wireless sensors, mesh routers, gateway and access to a secure data command center, where the actual component/location database resides. Sensors are battery-powered, wireless, intelligent fuse or circuit monitors, each with a unique ESN number that represents a unique location. Local indication displays a blown fuse or operated device condition. Sensors for fuses clip on the fuse body; sensors for circuit breakers must be wired in. Whether monitoring fuses or breakers, the sensor detects voltage to determine if the protective device has operated. If voltage is present on both sides of the protective device, the device has not operated, and the circuit is intact. If the protective device operates, voltage is present on only one side of the device. The sensor detects this and sends a signal that is picked up by the wireless mesh router, which, in turn, sends the signal to the gateway. The system operates in the 900 MHz band.
The system communicates with the mesh with a one-way transmission from the monitoring sensor, which makes the device more cost-effective. The sensor is not part of the mesh. The gateway resides behind the firewall and monitors the sensors and the mesh. It connects through the Internet to the servers at the command center, which is accessible by the end user. The high-security command center monitors fuse or breaker activity, alerts appropriate personnel when a circuit opens and provides historical data from which trending reports can be generated.
The alarm sent by the command center is typically an audible voice message in the form of a phone call. Alerts can also be made through email, pager or text message. If the person to whom the message is not available or does not acknowledge the alarm, the system's escalation feature deploys the alert to the next level of support personnel.
See wireless feature articles from Control Engineering : www.controleng.com/wireless .
— Edited by Mark T. Hoske, editor in chief
Jack Smith, Plant Engineering , contributed.
|Search the online Automation Integrator Guide|
Case Study Database
Get more exposure for your case study by uploading it to the Control Engineering case study database, where end-users can identify relevant solutions and explore what the experts are doing to effectively implement a variety of technology and productivity related projects.
These case studies provide examples of how knowledgeable solution providers have used technology, processes and people to create effective and successful implementations in real-world situations. Case studies can be completed by filling out a simple online form where you can outline the project title, abstract, and full story in 1500 words or less; upload photos, videos and a logo.
Click here to visit the Case Study Database and upload your case study.