Plant Controls in the Home Office?
Building-automation system (BAS) specification for commercial buildings has a long history of borrowing from more advanced concepts developed for the process industries.
Building-automation system (BAS) specification for commercial buildings has a long history of borrowing from more advanced concepts developed for the process industries. Yet, Southern California Edison (SCE) was making a novel-if quite logical-choice when they selected a BAS model for their general offices that more closely resembled the controls schemes used for their generation and transmission assets.
According to Stephen Long, P.E., systems integrator with Anaheim, Calif,-based Consolidated Data Systems, SCE moved away from a standard, single-source BAS approach in favor of a highly fault-tolerant open system that could control mechanical systems as well as fire- and life-safety equipment in its data-processing center.
The specified system employs a Windows-based human-machine interface (HMI) and an I/O server that sits between the HMI and all field controllers, says Long.
"SCE can go with any manufacturer of PLCs [programmable-logic controllers]," says Long of the open architecture. "They have tremendous flexibility, and can choose from multiple levels of very price-competitive PLCs that can be tailored to each application," regardless of whether it needs a high- or low-level controller.
According to David L. Toth, manager of design and construction with SCE, the decision mainly hinged on the system's track record and the utility's previous experience with it. "We basically used [this BAS system] because it worked," he recalls. "We had it in place in other areas and we had already researched it."
The automation system is laced through the entire complex via fiber-optic cabling, adds Rodney A. Sleeter, facility manager with SCE, which is uncommon for mechanical-system controls. "We have four operator stations, and they're hanging on [uninterruptible power-supply] units to keep the network up and alive at all times," he adds. "The HMI is very user-friendly, and the system lets us work with industrial process-control devices, which we are already familiar with."
Case Study Database
Get more exposure for your case study by uploading it to the Control Engineering case study database, where end-users can identify relevant solutions and explore what the experts are doing to effectively implement a variety of technology and productivity related projects.
These case studies provide examples of how knowledgeable solution providers have used technology, processes and people to create effective and successful implementations in real-world situations. Case studies can be completed by filling out a simple online form where you can outline the project title, abstract, and full story in 1500 words or less; upload photos, videos and a logo.
Click here to visit the Case Study Database and upload your case study.