Protecting Data-Processing Facilities
Prior to the implementation of the Montreal Protocol, Halon was the fire-suppression system of choice for computer and data-processing facilities throughout the United States.
Prior to the implementation of the Montreal Protocol, Halon was the fire-suppression system of choice for computer and data-processing facilities throughout the United States. With the cessation of Halon production, computer and data-processing facilities are now being protected by a variety of fire-extinguishing systems, including the available Halon alternative agents, and preaction sprinkler systems.
The Halon alternative agents are typically used in total-flooding applications, either total flooding of the computer room, underfloor spaces or equipment spaces or a combination of the above. These gaseous agents include halocarbon products and inert gas mixtures. The total-flooding agents, like the Halon systems they are replacing, are discharged into the protected space upon activation of fire-detection systems.
Preaction automatic fire-sprinkler systems are also being used for the protection of computer and data-processing facilities. Preaction sprinkler systems incorporate a preaction valve assembly that holds water back from the sprinkler system piping in the protected space until a detection system senses a fire condition and initiates the opening of the preaction valve. Water can flow into the system piping, but only discharges after the sprinkler head actuates due to the presence of heat at the individual sprinkler. Additional protection from inadvertent water damage can be provided with a double-interlocked preaction system, which holds water back from the piping until air pressure in the piping is relieved by the actuation of a sprinkler head.
In many computer applications, preaction systems can allow for power to be immediately disconnected from the computer equipment prior to filling the piping with water and discharging water into the room through actuated sprinklers. This power disconnect recognizes the fact that live computer equipment is more susceptible to water damage than equipment that is powered down prior to getting wet.
Whatever the extinguishing medium, computer and data-processing facilities can now also take advantage of new fire-detection technologies, which provide for earlier warning of equipment malfunction and incipient fire conditions.
|Search the online Automation Integrator Guide|
Case Study Database
Get more exposure for your case study by uploading it to the Control Engineering case study database, where end-users can identify relevant solutions and explore what the experts are doing to effectively implement a variety of technology and productivity related projects.
These case studies provide examples of how knowledgeable solution providers have used technology, processes and people to create effective and successful implementations in real-world situations. Case studies can be completed by filling out a simple online form where you can outline the project title, abstract, and full story in 1500 words or less; upload photos, videos and a logo.
Click here to visit the Case Study Database and upload your case study.