Transducer block specification issued
The specification by Fieldbus Foundation is designed for wired HART and WirelessHART devices along with updates to the WIO System Architecture and Data Structures
The Fieldbus Foundation has issued a FOUNDATION Wireless and Remote I/O (WIO) preliminary specification addressing fieldbus transducer blocks for wired HART and WirelessHART devices, together with updates to the WIO System Architecture and WIO Data Structures related to the transducer block specification.
Part of the FOUNDATION for Remote Operations Management solution implementing wireless and remote I/O, the new technical specification defines a fieldbus transducer block used to represent HART devices within FOUNDATION for Remote Operations Management devices. Both wired HART and WirelessHART devices may be represented in this block. In addition, the specification describes the expected method for HART configuration tools and asset-managing hosts to access HART devices using the native HART command protocol transported through the FOUNDATION High Speed Ethernet (HSE) network. The specification also defines structures to identify and maintain HART device status in wired multi-drop networks as well as in WirelessHART mesh networks connected to FOUNDATION for Remote Operations Management devices.
Within the FOUNDATION architecture, H1 and HSE provide a distributed function block capability with HSE serving as a larger pipeline offering increased speed and throughput. The WIO development expands these capabilities by establishing open, non-proprietary specifications for a wired or wireless HSE backhaul network integrating various wireless FOUNDATION for Remote Operations Management devices with interfaces to wireless field device networks.
HSE provides a way to bring large concentrations of discrete and analog field I/O from modular devices back to the control room using a high-speed HSE connection. Employing HSE devices functioning like a smart remote terminal unit (RTU), the technology brings all forms of conventional I/O into the native fieldbus environment easily. This solution makes discrete-in, discrete-out, analog-in, analog-out and H1 fieldbus available over a common Ethernet network. The addition of remote I/O further tightens the integration of process instrumentation within a FOUNDATION control system infrastructure.
- Edited by Chris Vavra, Control Engineering, www.controleng.com
|Search the online Automation Integrator Guide|
Case Study Database
Get more exposure for your case study by uploading it to the Control Engineering case study database, where end-users can identify relevant solutions and explore what the experts are doing to effectively implement a variety of technology and productivity related projects.
These case studies provide examples of how knowledgeable solution providers have used technology, processes and people to create effective and successful implementations in real-world situations. Case studies can be completed by filling out a simple online form where you can outline the project title, abstract, and full story in 1500 words or less; upload photos, videos and a logo.
Click here to visit the Case Study Database and upload your case study.