Using ‘semi-wireless’ instrumentation
Many devices are not suited to battery powering, so is removing just the data cable enough? What are your options for semi-wireless devices?
With the growing number of wireless instrumentation devices now available, you may have noticed that most of the offerings are toward the less-complex end of the device spectrum, things like temperature and pressure sensors. More complicated things like flowmeters have been slower in coming.
The apparent method in this selection is that vendors are bringing out devices that are relatively inexpensive and have low power consumption, and as such are suitable for battery powering. Suppliers are showing you that these sensors don’t need wires of any kind, neither data nor power. The problem is that the list of field instrumentation technologies suitable for battery powering is pretty short.
Vendors have a very good handle on the power consumption characteristics of device radios. Once you’ve determined the amount of data to be transferred, the update rate frequency, and the amount of repeater traffic, you can calculate the power need very accurately and then lay this out against your various battery options. The killer for a self-contained device is that the sensing technology also has to take power from the same batteries.
Optimizing sensor power
Radios gain their efficiency by sending data in a matter of milliseconds and then going to sleep between transmissions. For maximum battery life, the transducer technology has to match that quick action, but all don’t. Characteristics vary widely, but all don’t snap into action immediately. The transducer and its processor circuitry may need to stabilize after the power goes on before their measurement is final and ready to send. That may only be a few milliseconds as well, but when multiplied over the number of times it has to happen, that can be an eternity relative to the battery life. Consequently, vendors that are serious about expanding their wireless capabilities are finding new ways to optimize these issues. Back in the days of loop power, these weren’t particular concerns but things have changed.
There are technologies that will probably never run on batteries. A large Coriolis or magnetic flowmeter will most certainly need external power, although the current needs of these products have gone down considerably in the last few years. So what are the opportunities for these semi-wireless devices that require external power?
Many such devices will likely never be made in an integrated wireless package. Adding a built-in radio doesn’t offer all that big an advantage over buying an add-on generic transmitter, although the vendor community will make that determination based on market demand.
External power does not have to be mains supplied. A solar panel and rechargable battery setup or similar approach may be sufficient in remote locations.
Removing the need to pull a new data cable is obviously an advantage, but the exact cost implications of that for an end user will be very specific to the given site and application.
In most plant situations, power sources are probably closer than a marshalling cabinet or relevant I/O connection point. However you don’t just plug instrumentation into the closest outlet. Most plants have instrumentation-grade power that runs in parallel to lighting and general circuits. Instrumentation-grade power is better conditioned, protected, and configured such that it can’t be turned off easily by mistake, which is far less critical for lighting circuits. So the distance and cost of pulling instrument-grade wiring to a device will also be site specific.
If you have a number of devices on a given unit that all need wireless communication, it may be simpler to use a wireless remote I/O terminal that gathers the data and sends it back using one wireless Ethernet radio rather than individual transmitters. Such systems are available from a range of suppliers.
Wireless instrumentation is a tool that can help advance control and monitoring in your plant. However, like all tools, it has its limitations. Use it for the right jobs, wherever those may be, after you have weighed all the relevant options.
|Peter Welander is process industries editor. Reach him at PWelander@cfemedia.com .|