Wireless helps plains exploration and production, 2 month ROI
Plains Exploration and Production (PXP) Company automated its steam injection metering and data acquisition systems with a large network of WirelessHART transmitters and industrial broadband radios for a 10-times increase in transmitter accuracy and return on investment in 2 months. Automation from ProSoft Technology and Emerson Process Management helped.
In the San Joaquin Valley located in the heart of central California, the nutrient-rich soil from which an estimated 12% of the nation’s agricultural products are derived also happens to be the largest petroleum producing region in the state. These vastly different industries converge in the South Belridge Field just outside of Bakersfield, where the sight of cattle grazing between wells can be seen. It is here that Plains Exploration & Production (PXP) Company transformed its steam injection metering and data acquisition systems into a highly sophisticated, automated process comprised of a large network of WirelessHART transmitters and industrial broadband radios.
Application: Oil recovery project
PXP’s Hopkins Lease, located in the South Belridge Field, consists of over 200 wells distributed over a little more than a square mile. As an enhanced oil recovery project, continuous steam injectors play a critical role in the amount of oil produced by a given well. Placed adjacent to each producing well, steam is injected into the surrounding reservoir to help mobilize the oil toward the producing well.
Originally, each injector was fitted with a chart recorder, which metered and recorded steam. To track these readings, operators were required to visit each of the approximate 120 injection wells every day to visually interpret the chart recorders’ graphical readings, log them on a clipboard, manually convert these measures to a flow rate, key them into a spreadsheet, and send it to the office in Bakersfield where a data entry clerk keyed the figures into a database.
Problem: Potential recording errors
This steam metering method was very personnel-intensive. The chart recorders themselves required recalibration every three months, and it was difficult to accurately interpret their readings. Secondly, concerns existed about data integrity from potential recording errors during the several hand-offs and manual entry steps required. Lastly, the process consumed much of the operators’ time and provided only one data point per day, so should a problem arise at a well, PXP suffered response lag times in dealing with the issues.
The project facilities engineer at PXP saw these inefficiencies as another opportunity to improve processes for PXP. After equipment investigation, analysis, and discussion with operations, he was able to implement a new wireless metering and monitoring system, employing the latest technologies to deliver a real-time system, resulting in substantial benefits to PXP. The opportunity to implement a wireless solution made deployment quick and economical. Without these technologies, separate power and communication lines would be run to each well, making the retrofit project very costly and time-consuming. Additionally, maintenance of the system without the miles of power and communication lines is eliminated.
WirelessHART, IEEE 802.11
With close coordination with operations personnel, the new, state-of-the-art automation system began as a pilot project, during which 10 Rosemount 3051S WirelessHART Pressure Transmitters were installed at four wells. Two transmitters were placed on each well to measure the downstream pressure at the wellhead and the upstream pressure before the steam passes through a choke. On dual stream wells, a third transmitter is installed so that each stream has its own downstream transmitter and a shared upstream transmitter. The pressure transmitters communicated through the self-organizing mesh network to the Emerson WirelessHART gateway, where the process variables, process diagnostics, and instrument diagnostics were converted to Modbus TCP/IP data. ProSoft Technology 802.11 industrial broadband radios connect gateways in the field to an industrial PC in the office a mile away, forming the backhaul network, or an alternate wireless communication system that moves data from points in the field to the business system.
During the pilot project, PXP brought in a company that tests steam levels and is able to report a true number for the amount of steam being injected to a well. PXP compared the steam test results for both the wireless transmitters and the chart recorders and found the transmitters’ readings to be around 10 times more accurate on average.
Michael Fischback, project facilities engineer, expressed surprise at the magnitude of the accuracy increase. From a reservoir perspective, inaccurate steam metering translates into expensive repairs. Over-injecting of steam also leads to higher than necessary operating costs. Under-injection results in missed production opportunities where oil that could have been extracted was instead left in the ground.
After the project was validated, and with relative ease, the plan was rolled out across approximately 120 wells. In total, 249 Rosemount WirelessHART transmitters were installed, with four gateways aggregating this data and three ProSoft Technology industrial radios to communicate this data to an industrial PC in the field office. From here, data transmissions are sent to PXP’s intranet, where it is tied into two ProGauge Technologies custom designed Web-based software packages. One enables operators to log in and view well data, print reports, and view alarms. The other is a statistical analysis tool with historical data, designed to provide a higher-level look at the field for trending. It provides a visual overlay of the well sites, enabling reservoir and production engineers to view data by clicking on a well, or they can trend data, calculate steam-to-oil ratios (SORs), and more.
A .csv file is generated daily and imported into PXP’s reporting database, from which allocations are determined and distributed to various internal and external entities.
The wireless part of the implementation took about a day.
“Installation of the Emerson pressure transmitters was merely a matter of removing a mechanical pressure gauge and screwing on the new instrumentation,” described Fischback. “Installation of the ProSoft radio was as simple as mounting the radios onto a backboard. The installation of the ProSoft radios took no more than a day.”
Bob Karschnia, Emerson Process Management vice president of wireless solutions, said, “Upstream oil companies have a limited amount of time to deploy any kind of solution to help them solve their problem, so the faster they can get that solution deployed, the better. The advantages of using both the ProSoft Technology solution and the Emerson Smart Wireless solution are the ease of deployment. Both solutions have a straightforward user interface that allows you to configure and set up the networks almost instantaneously. They are very highly engineered solutions that take the complexity out of the user’s hands and build them into the products.”
Jim Weikert, strategic product manager for wireless at ProSoft Technology, said, “A lot of companies who focus mainly on enterprise communications do so with the understanding that there is a large team of people who are schooled in deploying their systems.” Emerson and ProSoft take a different approach, Weikert said, “in that we understand that the automation person deploying the system is an expert in the field—in this case upstream oil and gas—but they should not have to be an expert in the wireless system. This creates an opportunity when you have two companies like Emerson and ProSoft that focus primarily on reliability and ease of deployment.”
The system allows operators to see performance problems more quickly and react with better priority and increased time efficiency.
Results: ROI in 2 months
In enhanced oil extraction projects, steam costs can account for 40%-65% of a producer’s costs and are responsible for much of the revenue derived from a well. As a result of the newly automated wireless process and data acquisition system, PXP expects to see oil production increase, in addition to the benefits of greater efficiencies and reduced costs. The savings will more than pay for the system within the first couple months of operation (return on investment, ROI, in 2 months), and the benefits will continue. The operation will benefit from:
– Reduced maintenance: Calibration cycles for the Rosemount WirelessHART transmitters, which were delivered pre-calibrated, are recommended by Emerson only once every 5 years; a dramatic improvement from the 3-month cycle suggested for the chart recorders.
– Real-time data: Improved response times and smarter decision-making: Live data feeds to the field office, where operators can monitor present well status or query a range of conditions. Predetermined setpoints trigger notifications for operators to see instantaneously if a well deviates from goals. Data is archived permanently and can be trended for better analysis and decision making down the road.
– Increased efficiencies: The new system gives operators the data they need to better prioritize their day as soon as they arrive on site rather than visiting all 120 wells, not really knowing where to start, freeing them to focus on more productive activities.
– Profitability stemming from greater accuracy and distribution of resources: At today’s prices, the cost of steam at Hopkins exceeds $10 million annually, and with the new system in place, PXP can distribute its steam with improved accuracy compared to the chart recorders.
Under review: Other applications
The Hopkins Lease is a significant asset of PXP’s in the central valley, and its long-term goal is to continually improve its operations with solutions such as this. PXP will be reviewing where deployment of this technology can benefit its other operations.
“We’re pleased to see the results of this,” comments Fischback. “It’s got our operations team excited. Deploying technology to help continuously improve our operations is a step in the right direction.”
After a successful pilot, PXP will be automating 25 new wells on the Hopkins Lease with wireless vortex meters
Emerson and ProSoft Technology also collaborated on a similar application in Singapore.
– Adrienne Lutovsky is with ProSoft Technology Inc. at www.prosoft-technology.com.