# PID math demystified, part 1

## You’ve seen the equations, but have you thought about how those elements work together? Part 1: The basic concepts and proportional control.

05/06/2013

Most process control engineers have been exposed to the basic equation in a form that looks something like this:

More than you want to swallow in one bite? Let’s break this down into the major components:

Output: u(t)  is the output of the controller at the end of the scan. If the output of the controller is a valve, then the output is the valve position that the controller is requesting after it has seen the inputs. In most controllers, this is actually the change in output from 50%. So if u(t) = 0 then the valve output is 50%; if u(t) = 1 then the valve output is 51%; and if u(t) = -2 then the valve output is 48%. You get the idea. But what’s important is that it’s not a change in output from the previous scan, but a new output.

Proportional

Kpe(t) is the proportional component, the P in PID. If you have a controller configured as proportional only, this is it. So let’s look at how this works.

Let’s start with my own misconception of how I thought it worked. When I imagine a controller, I picture myself turning a valve while watching a gage. I look at the gage, decide if I need more or less, turn that valve a little more or a little less, and then repeat the process until the gage shows the value I want. That sounds fundamentally logical, but it is not how a proportional only controller works. It’s more like if I were to look at the gage, subtract what it reads from what I want it to read, and then take that error over to a chart to look up a new value for the valve.

e(t) usually called error, is simply the difference between the setpoint and the process variable. It is the difference between where you are and where you want to be, right now, at this instant.

Kp gain, is a factor that is multiplied by the error to give you the new output, the new valve position. It’s that simple. The error at that instant of the scan is calculated and the new output is calculated.

Let’s look at an example of pseudo code to explore how this works:

Error = Setpoint - ProcessValue;

Output = K * Error;

This control algorithm is deceptively simple, yet it gives an immediate response to a setpoint change or a disturbance in the process. And if K is set correctly, will quickly move the process toward the setpoint. But, it won’t get the process to the setpoint because there has to be some error if the output is anything other than 50%.

Note: On some systems (though not often in modern systems), gain is expressed as proportional band. Proportional band is defined as the amount of change in the controlled variable required to drive the loop output from 0 to 100%. To convert between the two, gain = 100/PB.

Next week: Understanding I and D.

This post was written by Scott Hayes. Scott is a senior engineer at MAVERICK Technologies, a leading system integrator providing industrial automation, operational support, and control systems engineering services in the manufacturing and process industries. MAVERICK delivers expertise and consulting in a wide variety of areas including industrial automation controls, distributed control systems, manufacturing execution systems, operational strategy, and business process optimization. The company provides a full range of automation and controls services – ranging from PID controller tuning and HMI programming to serving as a main automation contractor. Additionally MAVERICK offers industrial and technical staffing services, placing on-site automation, instrumentation and controls engineers.

Anonymous , 05/13/13 07:16 PM:

Please post simple analog (op amp) circuits for each of the PID sections. or A full opamp analog PID controller. Your description along with the circuit diagram of an old school analog (variable pot) design would greatly help the newbies with real world understanding. AS it did for me in the 70's. Thank you.
Anonymous , 05/14/13 07:59 AM:

This is a nice start on the series, but there is a trap. You have chosen one particular form of PID equation. There are, unfortunately, many forms, and they go by many different names. Once you get beyond proportional mode, you have to acknowledge those differences. Even in proportional mode, remember that some systems use proportional band instead of gain.
Anonymous , 05/14/13 11:29 AM:

P conttoller does no action until there is an error. This base need is satisfied by using manual reset
Dr. Zahid , AL, Pakistan, 05/17/13 10:19 PM:

These articles of PID are a quick source of information and good to read them
J. , NY, United States, 08/08/14 01:36 PM:

My limited experience is that of the 3 function P,I,D, the Derivative can be very disruptive and cause severe instability if over applied: use the derivative function sparingly if possible. Are there users of 'Feed Forward' who might comment?
Thank you.
The Engineers' Choice Awards highlight some of the best new control, instrumentation and automation products as chosen by...
The System Integrator Giants program lists the top 100 system integrators among companies listed in CFE Media's Global System Integrator Database.
Each year, a panel of Control Engineering and Plant Engineering editors and industry expert judges select the System Integrator of the Year Award winners in three categories.
This eGuide illustrates solutions, applications and benefits of machine vision systems.
Learn how to increase device reliability in harsh environments and decrease unplanned system downtime.
This eGuide contains a series of articles and videos that considers theoretical and practical; immediate needs and a look into the future.
Controller programming; Safety networks; Enclosure design; Power quality; Safety integrity levels; Increasing process efficiency
Additive manufacturing benefits; HMI and sensor tips; System integrator advice; Innovations from the industry
Robotic safety, collaboration, standards; DCS migration tips; IT/OT convergence; 2017 Control Engineering Salary and Career Survey
Featured articles highlight technologies that enable the Industrial Internet of Things, IIoT-related products and strategies to get data more easily to the user.
This article collection contains several articles on how automation and controls are helping human-machine interface (HMI) hardware and software advance.
This digital report will explore several aspects of how IIoT will transform manufacturing in the coming years.
Infrastructure for natural gas expansion; Artificial lift methods; Disruptive technology and fugitive gas emissions
Mobility as the means to offshore innovation; Preventing another Deepwater Horizon; ROVs as subsea robots; SCADA and the radio spectrum
Future of oil and gas projects; Reservoir models; The importance of SCADA to oil and gas
Automation Engineer; Wood Group
System Integrator; Cross Integrated Systems Group
Jose S. Vasquez, Jr.
Fire & Life Safety Engineer; Technip USA Inc.
This course focuses on climate analysis, appropriateness of cooling system selection, and combining cooling systems.
This course will help identify and reveal electrical hazards and identify the solutions to implementing and maintaining a safe work environment.
This course explains how maintaining power and communication systems through emergency power-generation systems is critical.